Nullifire SC802 Intumescent Basecoat is a water-based, fire resistant, white, thin film intumescent coating for the protection of internal structural steelwork.
SC802 intumescent paint for steel beams provides up to 60 minutes fire resistance. is applied to a smooth matt finish. If a decorative finish is required, apply a compatible top-seal such as: Nullfire TS816 Topseal, or Palatine’s Nullifire Approved Topseal (comes in a range of colours and finishes).
- Water based intumescent coating
- For internal steel
- Fire resistant for up to 60 minutes.
- “Next generation” product – with greater efficiency on site
- Compatible with a full range of Nullifire primers and top seals
- Very low VOC
Part of our Nullifire basecoats and Thermoguard Topcoat range.
Palatine Paints: Nullifire Approved Supplier
As a Nullifire authorised supplier, Palatine Paints makes the process easy for you whatever your experience or background.
You will be supplied with the Manufacturer’s certification on completion of your project free of charge. No need to worry about using incorrect quantities or chasing up paperwork… you can get on with doing what you do best.
Please Note: If you require certification, you must complete an intumescent enquiry form prior to your order. This ensures you apply the correct quantity needed to achieve the fire rating. The enquiry form is available to download from the ‘Data Sheets’ tab.
Apply only on dry and protected structural steel in temperatures of 5ºC and above. For best results apply by Airless spray. Ensure you mechanically stir before use. DO NOT THIN
Airless spraying: SC802 may be applied up to a maximum wet film thickness (WFT) of 1.0mm in a single spray coat of several quick passes. Achieving maximum loadings will depend on site conditions. Most 60 minute loadings can be applied in one coat
For brush application: Use a ‘laying on’ technique to avoid heavy brush marking. The maximum wet film per coat when applied using a brush or roller is 0.6mm. A short pile roller will produce a light textured finish. During application, measure the wet film thickness frequently (gauge provided) to ensure correct thickness is being applied